Restriction Orifice Calculator  Find Orifice Size
Size Restriction Orifice Calculation
You can share this calculator through:
Programmed by Iñaki Eseberri
He is a Process Control Lover experienced in complex and high profitable automation systems in the chemical and plastics industry. For a few years now, he has been an Associate Professor at the University' Fluid Mechanics Department and Director of a Postgraduate Degree in Industrial Control.
 Rating: 4.8  93 reviews
Contents
 How to calculate the Restriction Orifice Size?
 Calculator

Information and Definitions
 Tagname
 Plant, Area and Notes
 Fluid
 State
 Flow
 Temperature
 Pressure
 Dynamic Viscosity
 Density
 Ratio of Sp.Heats (kappa)
 % of Water in Wet Steam
 Pressure Tappings
 Pipe Diameter
 Bleed hole size
 Transmitter range
 Linear Expansion Coefficient for Plate (alphaplate) and for Pipe (alphapipe)
 Ambient Temperature
 Pipe Orientation
 Internal Pipe Diameter
 Pressure Ratio
 Pressure Drop Ratio
 Reynolds (ReD) and Reynolds Flow Regime
 Steam Correction Factor
 Expansibility Factor
 Discharge Coefficient
 Beta Ratio (Beta) and Estimated Beta (Beta0)
 Beta % Error
 Orifice Diameter at T
 Orifice Diameter at T0
 Limits of Use
 Restriction Orifice Calculator References
How to calculate the Restriction Orifice Size?
This calculator let you calculate the restriction orifice size based on pressure drop and flow rate.
The flow measurement using an orifice plate is based on the application of energy conservation to a flow, measuring the difference in pressure between two points (P1 and P2), at this points the flow has different speeds. This speed change is caused by a reduction in area. The orifice plate installed in the pipeline causes an increase in flow velocity and a corresponding decrease in pressure.
The equation that governs the use of these devices will be Bernoulli's equation in case of incompressible flows (liquids) or the first law of thermodynamics in compressible flows (gases). It should be noted however that the energy equation can be written in a very similar way to the Bernoulli equation under certain flow conditions, therefore the equation used in common practice comes from the Bernoulli equation and a factor to correct the compressibility of the fluid.
Orifice plates are still the most widely used type of flowmeter in the world today.
Request now your Results Spreadsheet Document!
Below you have our Restriction Orifice Pressure Drop Calculator. We have prepared a customized document with your own data, so you can do your calculations and then free download them for your own purposes.
Identification Data
Fluid Data
Instrument Data
Calculations
Information and Definitions
Tagname
Tagname of the instrument. This is the identifier of the field device, which is normally given to the location and function of the instrument.
Plant, Area and Notes
Information Referred to the physical installation of the instrument. Plant and Process Area where the instrument is installed. Notes about the instrument.
Fluid
Fluid Name or Composition. Fluid is called a type of continuous medium formed by some substance whose molecules have only a weak force of attraction.
A fluid is a set of particles that are held together by weak cohesive forces and the walls of a container; The term encompasses liquids and gases.
State
State of the matter. It could be Liquid, Gas or Steam.
Flow (qm)
Mass of a substance which passes per unit of time. Mass flow in Kg/s units, flowing through the pipe.
...where W is Mass Flow Rate, rho is Density and Q is Volumetric Flow Rate.
Temperature (T)
Operating Temperature of the fluid in Celsius units. The flowing temperature is normally measured downstream from the orifice and must represent the average temperature of the flowing stream in degrees Celsius. Temperature has two effects on volume. A higher temperature means a less dense gas and higher flows, but when this higher flow is corrected to base temperature, the base flow is less.
Pressure In (P1)
Considering the direction of the fluid, we define P1 as the pressure (gauge or absolut) existing in the pipeline before the restriction orifice.
Pressure has two effects on volume. The higher pressure makes the gas denser so less volume flows through the meter. However, when the volume is expanded to base pressure, the volume is increased.
Dynamic Viscosity (mu)
Viscosity is the measure of a fluid's resistance to flow. Dynamic viscosity is a measure of internal resistance.It measures the tangential force per unit area required to move one horizontal plane with respect to an other plane.
It is commonly expressed, particularly in ASTM standards, as centipoise (cP) since the latter is equal to the SI multiple millipascal seconds (mPaÂ·s).The viscosity of a fluid is highly temperature dependent.
Density (rho)
Density is the relation of mass and volume.The density of a material varies with temperature and pressure. This variation is typically small for solids and liquids but much greater for gases.
...where rho is density, m is mass and V is volume.
Ratio of Sp.Heats (kappa)
Ratio of the heat capacity at constant pressure (CP) to heat capacity at constant volume (CV). It is sometimes also known as the isentropic expansion factor and is denoted by Î³ (gamma) for an ideal gas or Îº (kappa), the isentropic exponent for a real gas. .
% of Water in Wet Steam (W)
Wet steam is a mixture of steam and liquid water. It exists at a saturation temperature containing more than 5% water. It is said to be a twophase mix: steam contains droplets of water that have not changed phase. % in volume of water present in steam.
Pressure Tappings
The pressure taps are placed before of the orifice plate (upstream) represented with P1 and after the orifice plate (downstream) represented with P2. In ISO 5167 there are three choices for the tappings:
1. Flange tappings
They are used more frequently because it is one of the simplest configurations and it is not necessary to drill the pipe. The high pressure outlet (H) is located 1 inch (25.4 mm) before the plate and the low pressure (L) 1 inch (25.4 mm) after the plate. With a tolerance of 0.5 mm when Beta larger than 0.6 and D less than 150 mm and 1 mm in other cases. They cannot be used for pipe size of less than 35 mm diameter. Since the venacontracta may be closer than 25 mm from the orifice plate.
2. Corner tappings
In this case the pressure taps are made directly at the edge of the plate by piercing the flange through independent holes made with a small inclination. These taps are similar in many respects to flange taps, except that the pressure is measured at the â€˜Cornerâ€™ between the orifice plate and the pipe wall. Can be used for diameters of less than 50 mm. The diameter of the holes a must be between 0.005 D and 0.03 D for Beta less than 0.65, and between 0.1 D and 0.02 D for Beta greater than 0.65.
3. Radius tappings (D and D/2)
The taps are made in the pipeline at fixed distances of 1 D before the orifice plate and 1â„2 D after the orifice plate. There is however a tolerance of 0.9 D to 1.1 D for upstream tap and for the downstream tap we will use 0.48 D to 0.52 D for Beta Ratio less than 0.6, and 0.49 D to 0.51 D, for Beta Ratio larger than 0.6.
As a rule of thumb Corner tappings are recommended for sizes up to 1 1â„2â€, Flange tappings from 2" to 16" and Radius tappings for higher sizes.
Orifice plate edge shape
The edge of the orifice plate generally has a special shape in order to minimize contact between the fluid and the orifice plate. This is usually done by chamfering at an angle of approximately 45 degrees at the edge of the orifice so that the edge is as narrow as possible, keeping the resistance of the plate.
Pipe Diameter (Dm)
Inside diameter of the pipe. All process calculations are based on the volume of the pipe which is the function of internal diameter of the pipe. As per standards, any pipe is specified by two nondimensional numbers Nominal Diameter (in Inches as per American Standards or mm as per European standards) and Schedule (40, 80, 160,...). The outer diameter of the pipe is the diameter of outer surface of the pipe.
Bleed hole size (y)
Size of the purge orifice in mm. The bleed hole is required in gas flow services where we can have trapped liquid. Bleed hole is not recommended in dirty fluid service or slurries as the hole could be plugged.
Transmitter range (DP)
We can design our orifice plate based on Pressure transmitter range, in this case we will introduce the span of the transmitter in the cell.
We can design our orifice plate based on Pressure transmitter range, in this case we will introduce the span of the transmitter in the cell.
Linear Expansion Coefficient for Plate (alphaplate) and for Pipe (alphapipe)
The coefficient of Linear thermal expansion describes how the length of an object changes with a change in temperature. Specifically, it measures the fractional change in size per degree change in temperature at a constant pressure.
Ambient Temperature (T0)
Ambient temperature is the air temperature of any object or environment where equipment is stored. The adjective ambient means "relating to the immediate surroundings." Also sometimes referred to as the ordinary temperature or the baseline temperature, this value is important for system design and thermal analysis.
Pipe Orientation
In this cell you can tell us how the orifice plate regarding pipe is installed it can be installed horizontal or vertical.
Horizontal
Vertical
Int Pipe Diameter (D)
Internal pipe diameter in mm. It has in consideration the thermal expansion of the pipe.
Pressure Ratio (PR)
Pressure Ratio at which the discarge coefficient determined has the value C.
Pressure Drop Ratio (PDR)
Pressure Drop Ratio (PDR=DP/P1) let you know the need to use compressible equations. For PDR less than 0.2 the change in gas density is small, and the assumption of incompressible flow can me made. For PDR greater than 0.4, the density change is large and compressible flow should be assumed.
Reynolds (ReD) and Reynolds Flow Regime
The Reynolds number (Re) is an important dimensionless quantity in fluid mechanics used to help predict flow patterns in different fluid flow situations. It is defined as :
...where rho is density, V is velocity of fluid in pipe, D is pipe diameter and mu is dynamic viscosity.
At low Reynolds numbers, flows tend to be dominated by laminar (sheetlike) flow, while at high Reynolds numbers turbulence results from differences in the fluid's speed and direction, which may sometimes intersect or even move counter to the overall direction of the flow.
There are in general three types of fluid flow in pipes
Laminar : 0 <= Reynolds Number <= 2300
Transitional : 2100 <= Reynolds Number <= 4000
Turbulent : 4000 <= Reynolds Number
Steam Correction Factor (Fs)
Only applies to Steam service. It only applies to the Steam service. Factor used in the calculation of the Beta Ratio to take into account the amount of water in the steam flow.
Expansibility Factor (eps)
Also called the expansion factor. The expansion factor corrects for the density change between the measured tap density and the density at the plane of the orifice face.
Discharge Coefficient (C)
The discharge coefficient is a dimensionless number used to characterise the flow and pressure loss behaviour of nozzles and orifices in fluid systems.It depends on the orifice shape. The discharge coefficient can be obtained for any differentialpressure meter and any installation by calibrating it in a flowing fluid: for a particular orifice meter the discharge coefficient is a function of the Reynolds number.
Over many years of experiment it has been found that the discharge coefficient can be predicted within a defined uncertainty provided that the orifice meter (i.e. the orifice plate and pipework) are constructed within the standards. If the discharge coefficient is to be used for an orifice meter without calibrating it in a flowing fluid, the discharge coefficient is usually taken from a published discharge coefficient equation. Therefore, the discharge coefficient equation is very important for orifice plates: an error of 0.1 % in discharge coefficient gives an error of 0.1 % in many flow measurements of natural gas. ISO 51671:2003 provides an equation for the orifice discharge coefficient calculation, Cd, as a function of Beta Ratio, Reynolds number, L1 and L2, where L1 is the distance of the upstream pressure tap from the orifice plate and L2 is the distance of the downstream pressure tap from the orifice plate.
Beta Ratio (Beta) and Estimated Beta (Beta0)
Beta Ratio is the ratio between the line inner diameter to bore size of the orifice. The flow coefficient is found to be stable between beta ratio of 0.2 to 0.7 below which the uncertainty in flow measurement increases. An orifice plate beta ratio of 0.6 means that the orifice plate bore diameter is 60% of the pipe internal diameter.
...where Beta is Beta Ratio, d is orifice diameter and D is orifice diameter.
Beta % Error (errB)
Error obtained in the calculation of the final Beta Ratio (Beta) with respect to the Estimated Beta (Beta0).
Orifice Diameter at T (d)
Inside diameter of the orifice plate at fluid's temperature.
Orifice Diameter at T0 (dm)
Inside diameter of the orifice plate at ambient temperature.
Limits of Use
Calculation's Limits of Use according to ISO 51672:2003. Standard orifice plates shall only be used in accordance with this conditions. See page point 5.3.1 of ISO 51672:2003.
Restriction Orifice Calculator References
1. International Organization of Standards (ISO 51671). 2003. Measurement of fluid flow by means of pressure differential devices inserted in circular crosssection conduits running full â€” Part 1: General principles and requirements.
2. International Organization of Standards (ISO 51672) 2003. Measurement of fluid flow by means of pressure differential devices inserted in circular crosssection conduits running full  Part 2: Orifice plates.
3. American Society of Mechanical Engineers (ASME). 2001. Measurement of fluid flow using small bore precision orifice meters. ASME MFC14M2001.
4. U.S. Dept. of the Interior, Bureau of Reclamation, 2001 revised, 1997 third edition, Water Measurement Manual.
5. Michael ReaderHarris (2015) Orifice Plates and Venturi Tubes.
6. Miller, R. W., Flow Measurement Handbook, 3rd ed., McGrawHill, New York, 1996.
7. American Gas Association, AGA Gas Measurement Manual, American Gas Association, New York.
8. Wikipedia
9. Corrosionpedia
10. Orifice Plates and Venturi Tubes (2015)  Michael ReaderHarris
11. EMERSON Fundamentals of Orifice Meter Measurement
12. Search Data Center
Another calculators or articles that may interest you:
 Flow Converter, an easy Flow Unit Conversion Online Tool.
 Pressure Unit Converter, a simple and easy online pressure unit converter that let you convert several types of pressure units.
 Visit this practical Viscosity Unit Conversion online tool: Viscosity Converter.
 Density Converter, another of our FREE Online Unit Converter
 Absolute Viscosity of Common Gases, is a table that represents the absolute viscosity of some common fluids and his evolution against the temperature.
 This is a table of specific heats' ratio for common gases: Heat Capacity Ratio of Common Fluids
 Density of Common Liquids, an useful table that represents the density of some common liquids and their temperature.
 Here you ara a complete table with the molecular weigth of common gases, including air, steam and natural gas, and his formula Molecular Weigth of Common Gases
 Don't forget to visit this Thermal Expansion Coefficient Table
 Read an easy explanation about the difference between the distinct types of pressure in "Whats the difference between Absolute, Gauge and Differential Pressure?".
 How to convert actual flow to normal flow?, How to convert standard cubic meter to normal cubic meter?, How actual to normal flow conversion works? If you want to answer these questions don't forget to read Difference between Actual, Standard and Normal Flows
 Orifice Plate Installation Guidelines is a necessary set of rules if you need to install an Orifice Plate
 What is pressure compensation? and why temperature compensation is required? In this article are all answers